# Short Circuits, Ground Faults and Ground Fault Circuit Interrupter

Posted by PITHOCRATES - April 9th, 2014

# Technology 101

## AC Power uses Reciprocating Currents to produce Rotating Electromagnetic Fields

There is a police crime lab television show that can solve a crime from a single fiber.  Many crime lab shows, actually.  Where they use high-tech science and music montages to solve many a crime.  Which is great if you DVR’d the shows as you can fast forward through them.  And save some time.  In one of these shows the writers goofed, though.  Because they didn’t understand the science behind the technology.

Someone murdered a construction worker by sabotaging a power cord.  By cutting off the grounding (or third) prong.  The fake crime scene person said this disabled the ground fault circuit interrupter (GFCI) device in the GFCI receptacle.  Leaving the user of the cord unprotected from ground faults.  So when said worker gripped the drill motor’s metallic case while standing in water and squeezed the trigger he got electrocuted.  And when the investigator saw that someone had cut off the grounding prong of the cord he said there was no way for the GFCI to work.  Which is, of course, wrong.  For the grounding prong has little to do with tripping the GFCI mechanism in a receptacle.

If you look at an electrical outlet you will see three holes.  Two vertical slots and one sort of round one.  Inside of these holes are pieces of metal that connect to wiring that runs back to the electric panel in your house.  One of the slots is the ‘hot’ circuit.  The other slot is the ‘neutral’ circuit.  And the third slot is the ‘ground’ circuit.  Now alternating current (AC) goes back and forth in the wiring.  It will come out of the hot and go into the neutral.  Then it will reverse course and come out of the neutral and go into the hot.  Think of a reciprocating engine where pistons go up and down to produce rotary motion.  AC current does the same to produce rotating electromagnetic fields in an electric motor.

## The Current in our Electric Panels wants to Run to Ground

If the current can come out of both the hot and the neutral why aren’t both of these slotted holes hots?  Or both neutrals?  Good question.  The secondary winding on the pole-mounted transformer feeding your house has three wires coming from it.  The secondary is a very long wire wrapped many times around a core.  If you measure the voltage at both ends of this coil of wire you will get 240 volts.  They also attach a third wire to this coil of wire.  Right in the center of the coil.  So if you measure the voltage from this ‘center tap’ to one of the other two wires you will be measuring the voltage across half of the windings.  And get half of the voltage.  120 volts.

These are the three wires they bring into your house and terminate to your electric panel.  The center tap and the two wires coming off the ends of the secondary winding.  They attach each of the two ‘end wires’ to a hot bus bar in the panel.  And attach the center tap to the neutral bus.  They also connect the ground bus to the neutral bus.  A 1-pole circuit breaker attaches to one of the two hot bus bars.  Current travels along a wire attached to the breaker, runs through the house wiring, goes through the electrical load and back to the panel to the neutral bus.  So this back and forth current comes from the 120 voltage produced over half of the secondary coil of wire in the transformer.  Where as a 2-pole breaker attaches to both hot bus bars.  Current travels along a wire attached to one pole of the breaker, runs through the house wiring, through the electric load and back to the panel.  But instead of going to the neutral bus bar it goes to the other pole of the 2-pole breaker and to the other hot bus bar.  So this back and forth current comes from the 240 voltage produced across the whole secondary coil in the transformer.

Current wants to run to ground.  It’s why lightning hits trees.  Because trees are grounded.  The current in our electric panels wants to run to ground, too.  Which we only let it do after it does some work for us.  When we plug a cord into an electric outlet we are bringing the hot and neutral closer together.  Like when we plug in our refrigerator.   When the temperature falls a switch closes completing the circuit between hot and neutral through the compressor in the refrigerator.  So the current can run to ground.  Which is actually a back and forth motion through the conductors to create a rotating electromagnetic field in the compressor.  Which runs back and forth between one of the hot bus bars and the neutral bus bar in the panel.

## Ground Faults don’t trip Circuit Breakers when finding an Alternate Path to Ground

When we stand on the ground we are grounded.  We are physically in contact with the ground.  We can lie on the ground and not get an electric shock.  Despite all current wanting to run to ground.  So if all current is running to ground why don’t we get a shock when we contact the ground?  Because we are at the same potential as the ground.  And no current flows between objects at the same potential (i.e., voltage).  This is the reason why we have a ground prong on our cords.  And why we install a bonding jumper between the neutral bus and the ground bus in our panels.  So that everything but the hot bus bars is at the same potential.  So no current flows through anything UNLESS that something is also connected to a wire running back to a hot bus in the panel.

Of course, if there is lightning outside we don’t want to be the tallest object out there.  For that lightning will find us to complete its path to ground.  Just as electricity will inside our house.  This is the purpose of the grounding prong on cords.  And why we ground all metallic components of things we plug into an electric outlet.  So if a hot wire comes loose inside of that thing and comes into contact with the metal case it will create a short circuit to ground for that current.  The current will be so great as it flows with no resistance that it will exceed the trip rating of the circuit breaker.  And open the breaker.  De-energizing everything in contact with that loose hot wire.  Eliminating an electric shock hazard.  For example, you could have a fluorescent light with a metal reflector in your basement.  It could have a loose hot wire that energizes the full metallic exterior of that light.  If you were working in the ceiling and had one hand on a cold water pipe when you came into contract with that light you would get a nasty electric shock.  But if it was grounded properly the breaker would trip before anyone could suffer an electric shock.

Ground faults are a different danger.  Because they don’t trip the circuit breaker in the panel.  Why?  Because it’s not a short circuit to ground.  But current taking a different path to ground.  That doesn’t end inside the electric panel.  For example, if you’re using a hair dryer in the bathroom you may come into contact with water and cold water piping.  Things that can conduct electricity to ground.  And if you are in contact with these alternate paths to ground some of that current in the hot wire will not equal the current in the neutral wire.  Because that back and forth current will be going in and out of the hot bus.  And in and out of a combination of the neutral bus and that alternate path to ground through you.  Electrocuting you.  But because of your body’s resistance the current flow through you will not exceed the breaker rating.  Allowing the current to keep flowing through you.  Perhaps even killing you.  This is why we have GFCI receptacles in our bathrooms, kitchens and anywhere else there may be an alternate path to ground.

So how does a GFCI work?  When current flows through a wire it creates an electromagnetic field around the wire.  If you’re looking into the wire as it runs away from you the field will be clockwise when the current is going away from you.  And counter clockwise when coming towards you.  In an AC circuit there are two conductors with current flow.  And at all times the currents are equal and run in opposite directions.  Cancelling those electromagnetic fields.  Unless there is a ground fault.  And if there is one the current in the neutral will decrease by the amount running to ground.  And the electromagnetic field in the neutral conductor will not cancel out the electromagnetic field in the hot conductor.  The GFCI will sense this and open the circuit.  Stopping all current flow.  Even if the ground prong was cut off.

www.PITHOCRATES.com